1200 AMP PORTABLE SPLITTER-PANEL 208Y/120V X 12 X 100-AMP OUTLET: TILT-BACK DESIGN. 12 X 100A X 208Y/120V OUTLETS
1200 AMP PORTABLE SPLITTER-PANEL 208Y/120V X 12 X 100-AMP OUTLET . SCOPE OF DEGINE: All Bossltg Temp Power systems are assembled per UL1640 Standards. This 1200A PANEL BOARD is installed in a Nema 4 enclosure. Green ON/OFF indicator light to alert operators of power. 12 – 100A, 208Y/120v PIN/SLEEVER receptacles wired into sides of enclosure. This package in mounted to a metal rubber caster wheel cage frame that can be rolled by hand over solid surfaces. Unit has forklift pockets plus center point lifting eye. Total system is UL performance tested, electrical, static load and environmental weather test simulated. This Bossltg product will carry a NEMA 3R Environmental Rating. After testing, system is UL Labelled, palletized, metal strapped, then plastic wrapped for shipments.
SQUARE D – I LINE SWITCH GEAR – BREAKERS
NOTIFICATION OF DESIGN VARIATIONS: Bossltg supplies SPLITTER PANELS with amp rating of 1200a and below. Voltages 480v and 208v.
SPECIFICATIONS: 1200a PORTABLE 480V VOLT SPLITTER PANEL – 480 VOLT 12 X 100A, 3PH: Equipped with 12 x 100a, 480v PIN & SLEEVE receptacles.
TYPE: 2″ Metal square tubing designed cage with 4 rubber conductive type caster wheels. CART design with forklift pockets and a center point lifting eye with 4/0 grounding lug.
480V PIN/SLEEVE RECEPTACLES: Killark, Appleton, Hubbell or Crouse Brand, 100a, 3p/4w, 480 volt
PANEL BOARD: 1200a, MLO, 480V, 3ph, 3p/4w. 36 Circuits with 12 – 100a, 3p branch 480V breakers. Mounted within a Nema 4 Enclosure.
WIRING: All wire will be sized to 115% of amp load rating. THHN 90* wire type within system.
UL CERTIFICATION: Boss will assemble and text his product to UL1640 Portable Job-site Electrical Distribution Standards.
UL LISTED MARK: The UL Mark will be labelled to the 1200 AMP PORTABLE SPLITTER-PANEL 208Y/120V X 12 X 100-AMP OUTLET. This mark will have a serialized number so that OHSA can track this product through the UL Certification system.
FALSE-HOOD REPRESENTATION: Just because an electrical assembler uses all UL Certified Electrical Components does not represent a product to be UL Listed. The company that is assembling the product has to be UL Qualified by Underwriter’s Lab and confirmed with a UL File Listing. A UL Listed Printed Decal distributed by UL’s Authorized Printer that will show a recorded individual serialized tracking number with UL Assemblers Company name. This UL Label must be installed in open view of operator.