PORTABLE SPLITTER PANELS 480V – 60AMP-100AMP PIN SLEEVE
Our PORTABLE SPLITTER PANELS 480V – 60AMP-100AMP PIN SLEEVE are assembled to UL1640 and NEC National wiring Standards. This splitter panel has six 100 amp pin & sleeve receptacles mounted on a Nema 3R enclosure wired to six 100 amp 480v 3p Circuit breakers installed within a 600 amp load center, MLO. The Load Center is rated Nema 3R for outdoor use. System has a GREEN 480v pilot light to advise operators on site that power is live at panel.
The Boss PORTABLE SPLITTER PANELS 480V – 60AMP-100AMP PIN SLEEVE Load Center is attached to a two wheel ( conductive ) steel cart. Balance to where the system can be moved around hard services. This load center is protected from rain with a UL required bonnet. Bonnet is installed so falling rain cannot directly be exposed to opened circuit panel door.
480 volt Splitter Panels are painted Safety Red. 208Y/120v, 3ph panels are painted Safety Blue, and, 120/240v, 1ph panels are painted white.
For this product PORTABLE SPLITTER PANELS 480V – 60AMP-100AMP PIN SLEEVE can supply Square D I-line Gear or General Electric Gear depending on clients preferred Brand. Stab on or bolt on breakers clients choice. Wiring devices can be supplied using Appleton, Killark, Crouse Hinds, or Hubbell.
With advance notice Bossltr can assemble special required Splitter panels to meet clients specific need. We ask that you give us 14 day notice on any special built projects.
SPECIAL RENTAL PRODUCTS UPON REQUEST.
Bossltr can assembler Transformer substations using only 480 volt line power. We can add welding switchgear with fused disconnects or individual single breaker wiring outlets. We can supply both 480v, 3ph or 208y/120v, 3ph substations with transformers to allow for a bank of 120v or 240v GFCI receptions sized to transformer load capacities, or, we can use GFI breakers with WR duplex outlets as many has client request.
Boss is a UL1640 Temporary Job-site Electrical Distribution Assembler. We can assemble rental products to meet our clients specific job requirements. The following model # Splitter panel can be modified using clients required amp rating of panel and the individual wiring devices needed for applications.